To select a Highland Vertical Aboveground Steel Storage Tank, follow these easy steps:
Select desired tank volume - Specify single-wall, double bottom or double-wall construction
Select desired secondary containment system - Select desired internal and external protective coatings
Determine type, size, location and number of fittings and manways - Select accessories and options
A drawing showing the storage tank size, along with the type, size and location of the fittings and manways and accessories required is helpful when requesting a quote or placing an order. Please refer to the adjacent diagrams of some of the standard tank features and accessories available.
A.Tank Diameter - Ranging from 3'-2" to 14'-0"
B.Tank Height - Ranging from 3'-4" to 50'-0"
C.Manway - Diameters from 24" to 36"
D.Interior Coating - Specify Seal Welding, SSPC Cleaning Standard and type of Interior Coating
E.Interior Ladder - 2" x 1/4" sides – 3/4" rungs on 12" centers (OSHA requires a 36" diameter Manway for Interior Ladders)
F.Standard Threaded Fittings - Specify size, number, location
G.Flanged Fittings - 150 # A.S.A. Specify size, number, location
H.Fuel Oil Preheater
I.Leak Detection System - Specify Single or Multi-Channel system configuration
P.Exterior Ladder - (Outside of tank, with or without a platform)
Q.Ladder & Cage
U.Thermal Insulation System
W.Double-Wall Emergency Vent